A class I structure is 75 feet or lower True or False?
True
What is the weight of Class I Aluminum Conductor?
95Lbs/1000'
What is the weight of Class I copper conductor?
187Lbs/1000'
What is the weight per length of Class II copper conductor?
375lbs/1000'
What is weight per length of Class II aluminum conductor?
190lbs/1000'
What is the minimum diameter of solid copper Class II air terminals?
1/2 inch
What is the minimum diameter of Class II solid aluminum air terminal?
5/8 inch
What is minimum diameter of solid copper Class I air terminals?
3/8 inch
What is the minimum diameter of solid aluminum Class I air terminal?
1/2 inch
What is the minimum diameter of Class II tubular copper or aluminum air terminals?
None, not allowed
What is minimum diameter of Class I tubular Copper or aluminum air terminals?
5/8 inch
What is the minimum width of copper aluminum bonding plates?
1/2"
What is the height of a Class II structure?
Higher than 75 feet.
When a section of a structure e.g. a steeple exceeds only that portion above 75 feet must use class II hardware?
True or False
True
What is the minimum height above the object it protects must an air terminal must be ?
10 inches
A Heavy duty stack has the following height and opening size:
Higher than 75ft and 500 square inches.
An air terminal that is 36 inches tall needs intermediate support at 18 inches?
True or False ?
True
The maximum distance of an air terminal from the edge of a roof is how many feet?
2 feet
The maximum spacing of air terminals 24 inches tall or less along the edge of a roof is how many feet?
20 feet
The maximum spacing of air terminals taller than 24 inches along the edge of the roof is how many feet?
25 feet
The maximum distance of air terminals located within the roof parameter of a flat or gently sloping roof is how many feet?
50 feet
What slope is required for a roof 40 feet or less wide to be considered a pitched roof?
1/8
What slope is required for a roof > 40 feet wide to be considered a pitched roof?
1/4
No parameter strike termination devices are required on pitched roofs where the eave is 50 feet or less.
True or False
True
What is the maximum distance between intermediate air terminal on ridged roofs?
50 feet
For flat or gently sloping roofs, what is the maximum distance from a main parameter or down conductor that a cross connection conductor can be located?
150 Feet
What is the maximum distance from the edge of a roof projection that an air terminal can be located?
2 feet
Conductors shall be connected together with what what type of connectors?
Tee, Wye, end to end
Air terminals on chimney or HVAC units must be installed so no edge is more than 3 feet from the air terminal?
True or False
False, 2 feet maximum.
Air terminals or devices(chimney, HVAC, etc.) used as air terminals must be connected with how many main conductors to ground?
2
What thickness of metal must a device be to act as an air terminal or main conductor?
3/16 inch
Metal roof top units can have the air terminals installed by:
1. adhesive bases
2. metal bases with at least 3 square inches metal to metal contact.
3. Metal bases connected to the frame with drill and tapped 1/2" bolt with 5 threads fully engaged.
What minimum thickness of metal must the enclosure of metal enclosed roof top unit be to act as a down conductor?
0.064 inches
If a metal enclosed roof top unit is used as the down conductor or air terminal how must it be connected to the main conductor?
1. Connected at the base at two points as far away from each other as possible.
2. Each connector must make 3 square inches metal to metal contact.
buildings 25 feet or lower can have a zone of protection with a slope of:
1/2
Buildings taller than 25 feet but not exceeding 50 feet can have a zone of protection with a slope of:
1/1
The rolling sphere method normally uses a sphere with a radius of:
150 feet
The rolling sphere radius used for structures housing explosives is:
100 Feet
The formula for calculating the distance protected by a rolling sphere from one level to another is:
D=Sqrt[h1(2R-h1)]-Sqrt[h2(2R-h2)]
How many paths to the grounding electrode must an air terminal have?
2
What is the maximum length of main grounding conductor interconnecting one roof level to another before 2 paths to the grounding electrode are required?
40 Feet
The maximum horizontal length of a dead-end conductor from an air terminal to a main conductor located at the same level is:
8 feet
The maximum length of a dead-end conductor from an air terminal to a main conductor located a level below the level of the air terminal is?
16 feet
All dead end conductors must run a horizontal and upward direction.
True or False
False, run must be horizontal and downward.
Permanent handrails and ladders subject to lightning can be used as down conductor if their thickness is a minimum of:
.064 inches
Main conductors shall be run in _______ and ______ avoiding to make _____ pockets and ______ Pockets.
horizontal, down-ward U, V
The minimum radius of bends on main conductors is:
8 inches
conductors must be protected with ____ or ____ when within ____ of the top of a chimney or stack producing corrosive vapors.
Tin, lead, 24 inches
Copper must not run off into aluminum.
True or False
True
Aluminum conductors must not be within _____ of the ground/earth.
18 inches
Down conductor must be protected from damage for _____ above the ground.
6 feet
Moveable metal objects must be bonded to the LPS with main conductor making metal to metal contact of _______ or _______ for rounded surfaces.
3 sq inches, 1 1/2"
Cross run conductors connecting intermediate air terminals shall connected to parameter main conductor at intervals not exceeding ______.
150 feet
Each structure must have at least ______ down conductors.
2
Structures with parameter exceeding _____ must have down conductors no more then _____ apart.
250ft, 100ft
Flat or gently sloping roofs must have down conductors every _____.
100ft
Structures with roof 50ft to 100ft wide must have at least ____ cross conductor(s).
1
Structures with roofs 100 to 150 feet wide must have at least ______ cross conductors.
2
Metal siding or roof material less than 3/16" thick may be used as a main or down conductor.
True or False
False, must be at least 3/16" thick
exposed conductors must be fastened to the structure every ____.
3 feet
conductors coursed through the air must not exceed ______ without support.
3 feet
Ground rods must be ______ diameter and ______ long
1/2", 8 feet
How deep must ground rods be driven?
10 feet
Ground rods must be made of what materials?
Copper, copper clad steel, stainless steel
Fittings at Tee, Wye and end to end connections must be capable of withstanding ______ pulling force.
200lb
Tee, wye and end to end connectors shall be made with ________________________ connections
Bolted, welded, brazing, compression
Connection of the down conductor to the grounding electrode must be by_______________connections
Bolted, welded, brazing or high compression
Crimp type connections can be made on Class II systems.
True or False
False
At what distance must ground rods be seperated from each other?
The sum of the length of the ground rods or sum of burial depths.
What is the thickness and area of a ground plate?
0.32in and 2 sqft
How deep must a ground plate be buried?
18 inches minimum
A concrete encased electrode is ______ of main conductor encased by ______ of concrete.
20 feet, 2"
What is the minimum length and diameter of rebar in concrete that can be considered a concrete encased electrode?
20 feet and 1/2"
Down conductors entering corrosive soil must be protected for a distance of _______ with a a covering against the corrosive.
3 feet above grade.
What materials can be used to protect down conductors?
Wood platic or metal
Down conductors on steel reinforced concrete shall be bonded to the steel on the _____ and _____. For long runs bonding must occur every ______.
Top,bottom, 200 feet
Disconnects to the grounding electrode should be made at low as possible to limit false ground resistance reading.
True or False
True
LPS grounding electrode system can be any system e.g. power, communication etc.
True or False
False, it must be dedicated to the LPS.
The connection to the LPS grounding electrode system must be made at least_______ from the base of the building and ______ below grade.
2 feet, 1 foot
How much electrical contact must there be on connections to ground rods?
1 1/2"
How many bolts must be used to make connections to ground rods?
2
What size conductor on a class II system must the ground ring be?